Turbine Alternator Repair
On Site Repair Jobs executed
- Onsite Grinding/Repair of Turbine, Rotor and Alternator journals is under taken.
- Equipment available to execute on site repair of Turbine, Rotor and Alternator journal up to diameter of 700 mm and can be extended up to 1500 mm diameter.
- Tolerance in terms of Taper and Ovality is maintained with in 20 microns of Turbine, Rotor Shaft, Alternator Shaft resulting to minimizing of vibrations.
- Surface finish in terms of RA value maintained with in 0.30 microns after on site repair of Turbine Shaft, Alternator Journal, Rotor Shaft etc.
- On site Inspection facilities for crack detection, hardness and surface finish test.
- Facility for rebabbitting and manufacturing of white metal babbitt bearings.
More than 100 jobs have been successfully executed for Onsite Repair of Turbine Shaft, Rotor Shaft, Alternator Journal
Recently we have executed a in situ Repair of Turbine Journal
having following major specification:
||Shandong Jinan Power Equipment, China
|| 168.8 MVA
||Dia 315 mm, width 400 mm